Anybody who researches stoves with back boilers and radiators ends up reading about the injector T. Read on and find out more…
The manual is designed to be used alongside Document J of the Building Regulations coupled with any advice provided by your local Building Control. You should not rely on this manual alone. In the case of boiler stoves you will also need to familiarise yourself with Document G of the Building Regulations and any other relevant plumbing regulations.
So we have looked at the primary system and the heat sink radiator. As already suggested this is the foundation of any solid fuel system.
Adding radiators is quite a simple process. Let’s start with a scribble:
If your boiler stove has four ports on the rear then this makes life easy. Connect your flow and return to the two spare ports (primary circuit on other two already) and add a pump to the return pipe. The primary circuit is not affected by the pump because the stove is acting as a buffer between the two circuits (whether pump is on or off the gravity circulation continues as if the pump were not there). Both thermostats are connected to the pump.
The thermostat on the PRIMARY CIRCUIT RETURN switches the pump ON when the water returning from the heat sink is hot enough – this ensures that the pump only comes on when the stove is lit and prevents cold water being pumped around the stove which is not good as it encourages condensation within the stove. This thermostat is set at approx. 35-40 degrees centigrade. If the heat sink is a cylinder rather than a radiator then the thermostat ensures the pump does not come on until the cylinder has plenty of hot water (if set at 35-40 degrees). So although very simple in design we do have a “hot water priority” system.
The thermostat on the PRIMARY CIRCUIT FLOW switches the pump ON only if the flow pipe from the stove gets particularly hot. It is set at approx. 85 degrees centigrade. This “overheating” of the flow pipe can take place if the stove is burning out of control (e.g. the door has been left slightly ajar or the user has overloaded the stove with fuel). When the pump comes on the system is cooled (water passing through the radiators).
Unlike the primary circuit, the radiator circuit, due to being pumped, can follow any kind of path (up, down, multiple bends etc.) with trapped air being the only concern where pipes travel “up and over” (avoid this or ensure that at the top is some method of air release or collection).
Top tip: Running radiator pipes under floors is often fraught with problems. Joists are in the way and Building Regulations might not allow notching or drilling. One way around this is running pipes up into the loft (often following a chimney breast) and then dropping down from the loft into rooms below (often in corners where boxing is less obtrusive). Make sure your header tank is well above all of your pipes.
Let’s look at what to do if your stove only has two ports on the rear:
Now the pump DOES affect the gravity circulation.
The radiator flow pipe can branch off anywhere along the flow of the primary circuit. The radiator return must enter the primary return in the manner shown above: via an injector T. An injector T is a simple copper plumbing fitting that allows water to be pumped through it whilst sucking in water from its top opening. So in our scribble the pump pushes water into the stove whilst water is sucked in from the pipe coming in from above (this being the primary return). The injector T ensures that the gravity circuit is assisted by the pump and not interfered with. If the injector T is not in place then the pump pushes water into the stove and UP the primary return (and is interfering). Then this happens:
What happens here is that the water flow within the cylinder is reversed. Now a proportion of the cool water returning from the rads (rads have stolen heat) bypasses the stove and travels through the cylinder, stealing heat from the cylinder before travelling back trough the rads. It will still “work” but the cylinder will not benefit whilst the pump is on and may cool somewhat.